Hi, I'm Dave, I am a local handyman and state licensed HVAC tech with enough experience
in remodeling to tackle about any project in your home. Feel free to call me if you have a question or drop me an email. I
look forward to hearing from you!
Pay the amount you owe for service with a Credit Card
"I'm always looking for ways to help market my services. Thumbtack is a good way for
me to help me show off my expertise. Check out my profile to learn even more about what I do!"
For anyone who is looking for information that will help them
understand the components of your home and how everything works read this 25 book. It will also save you money on repairs
and utility bills.
Written for those who want there house to be a home.
Dave's Handyman Express 800-440-6515
I service the following areas:
N. Baltimore Findlay Tiffin RisingSun
Fremont Maumee Perryburg and all between
When you want quick, reliable service
-get a free estimate and very reliable help for most installation and remodel projects.
click on the cross to see the types of work I have the skill and ambition to complete-the
gift to make a living.
Dave's House 419-436-233
The HVAC GUY 1-800-440-6515
A good handyman follows local codes. If you find a problem tell the homeowner so they can get it fixed.
Don't leave a house without inspecting for obvious problems like old wired taped off in the basement or attic.
Code only allows any circuit to be loaded 80 % of its rated load. We understand that
most devices will not be on all the time, however, there only needs to be one time for all to be on to exceed the allowed
ampacity of the circuit, and to be sure there is absolutely no fire hazard, the 80% rule should be followed.
A 15 amp
circuit can carry a total of 1440 watts,which is 80% of the 1800 watts found by mulitplying the volts times amps,15
x 120 x 80%= 1440.
A 20 amp circuit can be loaded 1920 watts, 120 x 20 x 80%=1920 watts.
If the panel was
recently replaced there should have been a 15 amp breaker because code allows #14 wire, which can only use a 15 breaker,and
a 20 amp breaker cannot be connected to it.
The small furnace blower may pull up to 12 amps at start up, or "Locked
Rotor Amps". Motors need to be protected by a breaker 125% of the load, 12 x 125%= 15. This can use # 14 wire and a 15 amp
breaker, and should be alone on the circuit.